|Temperature Rating||68 DEGREE|
|Mounting Type||Ceiling Mounted|
|Country of Origin||Made in India|
A fire sprinkler system is an active fire protection measure, consisting of a water supply system, providing adequate pressure and flow rate to a water distribution piping system, onto which fire sprinklers are connected.
A wet pipe system is one in which water is constantly maintained within the sprinkler piping. When a sprinkler activates this water is immediately discharged onto the fire.
Advantages to using a wet pipe fire sprinkler system include:
1. System simplicity and reliability – Wet pipe sprinkler systems have the least number of components and therefore, the lowest number of items to malfunction. This produces unexcelled reliability which is important since sprinklers may be asked to sit in waiting for many years before they are needed. This simplicity aspect also becomes important in facilities where system maintenance may not be performed with the desired frequency.
2. Relative low installation and maintenance expense – Due to their overall simplicity, wet pipe sprinklers require the least amount of installation time and capital. Maintenance cost savings are also realized since less service time is generally required compared to other system types. These savings become important when maintenance budgets are shrinking.
3. Ease of modification – Wet pipe fire sprinkler systems are advantageous since modifications involve shutting down the water supply, draining pipes and making alterations. Following the work, the system is pressure tested and restored. Additional work for detection and special control equipment is avoided which again saves time and expense.
4. Short term down time following a fire – Wet pipe sprinkler systems require the least amount of effort to restore. In most instances, sprinkler protection is reinstated by replacing the fused sprinklers and turning the water supply back on.
Fire Sprinkler Systems have been the biggest breakthrough in fire protection in the last 100 years. Fire sprinklers are the most effective method of protecting lives and property. Sprinkler systems are now recognized as being so effective they are being made mandatory in many situations.
Every building should be classified for fire risk under the following categories: light hazard, ordinary hazard group and high hazard group. Factors involved in classifying a building''s hazard level include the material used in construction, the occupancy level, the materials stored in the building, the processes performed in the building (and whether these processes include flammable liquids), ceiling heights, ease of egress, and the amount of floors and rooms.
Fire safety standards indicate the colour of the bulb and the respective perating temperature:
Temperature °C 68 79 93 141 227 260
Temperature °F 155 174 200 286 440 500
Colour of liquid inside bulb Red Yellow Green Blue Black Black